We’re Proud to Serve Groveport, OH
If you’re looking for Heating, Cooling, or Indoor Air Quality Services in Groveport, OH, trust the experts at Upper Arlington Heating & Air. We specialize in the repair, maintenance, and installation of furnace, heat pumps, air conditioners, and more. We service all brands and types of HVAC equipment in Groveport, OH. We look forward to providing you with a trusted HVAC solution. Give us a call today!
Trust the experts. Call us today! (614) 490-7507
The City of Groveport has a population of 5,363 people. Another suburb of the City of Columbus, Groveport has a total area of a little less than nine square miles; it was the home of the historic horse expert, John Solomon Rarey, who earned acclaim during the 19th-century when he developed the well-known “Rarey Technique” for rehabbing horses.
In 1846, Groveport had its roots as a single entity, when then rivaling towns Wert’s Grove and Rareysport ended up merging together. Since 1847, a post office with the name Groveport has been in operation. The city houses the historic Groveport Log House, which was constructed in 1815. In 1974, it was moved to its current location near the Groveport Cemetery.
Because of the city’s proximity to the Air National Guard Base and Rickenbacker International Airport, several large corporations have made their headquarters or a significant part of their operations in Groveport, stimulating the local economy. Among these many major companies, there is Amazon.com, Eddie Bauer, Gap, Spiegel Brands, FedEx, American Electric Power, and VistaPrint.
Among the many things to do in Groveport, residents and visitors enjoy the Alum Creek bike trail, Three Creeks Metro Park, Motts Military Museum, Groveport Aquatics Center, and Walnut Woods Metro Park.
Upper Arlington Heating & Cooling is happy to serve the residents of Groveport, OH with the best local HVAC products and services at the most competitive rates in the area. We’re the preferred local HVAC contractor of choice in the Franklin County and Central Ohio area for heating and cooling services.
We offer same-day emergency services for cooling and heating equipment, 24 hours a day, 7 days a week, including weekends and holidays! Furthermore, we offer professional installation for those needing a new air conditioning system, heat pump, or furnace in Groveport.
We’re also excited to offer Groveport residents our year-round Service Maintenance Agreements if you’re looking to get the most from your air conditioning system, heating system, furnace, or any other HVAC system with preventative maintenance, which should be done every year to keep your manufacturer’s warranties in good standing.
for Groveport, OH
Dave - Groveport, OH
Hunter was professional and friendly. Five star technician.
Great Price and Service!
John - Groveport, OH
We needed to have the installation completed within a specified time window, and the team did an excellent job of ensuring that everything was complete and working properly ahead of the time needed. The area was clean when they left. We were also able to take advantage of some end-of-season pricing.
Great Service ! Great Service Tech !
Mark - Groveport, OH
Service Tech Very Knowledgeable Very Respectful Friendly and Courteous. Send Him Anytime to Service My Equipment.
Getting to the bottom of it
Brent - Groveport, OH
Tech Chris brought his supervisor Hunter with him to figure out why furnace keeps shutting off.
Brent - Groveport, OH
Robert - Groveport, OH
Was amazing to watch him check the system out.
Amanda - Groveport, OH
Showed up the same day and went above and beyond to get our new thermostat set up and our air back up and running.
Great Service - Reasonably Price
John - Groveport, OH
Service tech called ahead of time and arrived moments later. He was thorough and provided me with a detailed readout of what he had checked. I have used them previously and will probably again.
DIana - Groveport, OH
Pickerington H&C are responsive,thorough,neat,as well as knowledgeable.. They had my air conditioner back running great in under an hour..
Mark - Groveport, OH
Quick Easy Painless Experience
I completed a diagnostic. Upon arrival customer stated AC unit was not cooling the home. I found that the condenser fan motor nor compressor were running. Capacitor also tested bad. I notified customer that the capacitor is bad replaced capacitor. I found the refrigerant charge is low notified customer they were low on refrigerant. Charged system 2 pounds of R 22. System running and operating normal.
I completed a diagnostic. I found the low voltage fuse was blown at the circuit board. I shut down the furnace and replaced the fuse. I pulled slack out of the wall at the thermostat, cut straight and clean wires, plenty of leftover slack for future thermostats. Nest thermostat installed, wired furnace and Nest to match the equipment. System operating upon departure.
I completed spring tune up on a Lennox air conditioner. I visually inspected the furnace. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked voltage and amps. Inspected heat pump. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating normally at this time.
I arrived on site to perform an estimate for a Rheem air conditioning unit. Due to the age of the unit and the numerous issues being discovered during the inspection the customer opted to replace the unit. Unit not operational at the time of departure.
I arrived on site to perform an inspection on a Carrier air conditioning unit. During the inspection I found that the unit was running constantly during the day due to the unit being overworked temperature wise. I adjusted the thermostat to help resolve the issue, and informed the customer to call us back if the situation does not improve.
I arrived on site to perform an inspection on a Bryant air conditioning unit. During the inspection I found that the unit's low voltage wires were removed from the unit, not providing power to the unit and making it unable to function properly. I reattached the wires and the unit was running at full functionality at the time of departure.
I completed a return service on an air conditioner. I found that everything was operational.